Ridgevalley Reverse Osmosis Water Treatment System
- Installation: 2017
- Location: Alberta
- System: Direct feed dual train RO system
- Permeate Flow Rate: 436 m3/day or 4.8 L/s
The Municipal District of Greenview, a growing community, realized the need to upgrade the existing Ridgevalley Water Treatment Plant. They required a reverse osmosis water treatment system to be installed adjacent to the existing water treatment facility, in a proposed expansion building. Sapphire Water provided a dual train RO system to effectively expand the municipalities water treatment capabilities.
|Parameter of Interest||Raw Water||Permeate||Guidelines|
|TDS (mg/L)||853||389.96||≤ 500|
|Sodium (mg/L)||360||135.23||≤ 200|
|pH||8.7||8.38||6.5 – 8.5|
|DOC (mg/L)||5.3||<2||< 5*|
* No criteria in Canadian Drinking Water Guidelines. Reduction required for chlorination bi-products formation prevention.